Glow-worm prides itself as
the manufacture of wide range of user-friendly heating appliances. Glow-worm is
the sister brand of internationally renowned Vaillant group. Both of the brands
are highly recommendable by the installers and the users.
The fundamental feature of
Glow-worm is producing the boilers which are comprehensive and easy-to-control.
All the boilers are highly reliable and efficient that has been developed to
save maximum amount of energy possible by the innovative technology standards.
The products here are designed
and manufactured to serve the customers with maximum and smart control over the
unit. The brand comes being known for its remarkable reliability and efficiency
that make it a desirable brand and considerable choice in the market.
You might be wondering about how to repressurise a glow
worm 30cxi boiler and how to repressurise a glow worm boiler 24cxi.
the very first note, the process of re-pressurizing for the 30 and 24 output
ranges of Glow worm cxi boiler is same as the models differ just in the output
In case if your central heating system is not
working properly, it could be because of the loss of water pressure. You need
to check the water pressure indicator on the front of your boiler that, for a
normal good working boiler, should read between one or two bars of atmospheric
If the boiler pressure is below one, this indicates
the pressure in your boiler is very low. In this case you need to re pressurize
you might be thinking how to repressurise a Glow worm cxi boiler?
You just need to follow certain easy steps in order
to deal with the method of re-pressurizing.
- Close all the vents
getting start with re pressurizing your boiler, check all the bleed valves on
radiators and towel rails to be fully closed.
- Search for the filling loop
most of the boilers, they have the external filling loop that is used to top up
the boiler with water and hence increases the pressure.
soon as you open the filling loop, you will get to see a pressure rise. You can
take a look of what is the exact pressure your boiler needs. Commonly the
boilers operate with 1.5 bars.
sure that the filling loop is completely closed. However if it is not closed it
will slowly leak additional water into the boiler. This will increase the
pressure and the boiler will lockout.
–If there is no filling loop in your boiler, they might be installed on the
you have re pressurized your boiler too much you will need to drain the system.
But if the pressure is very high by less than 0.5 bars, you need to understand
the problem by bleeding radiators. You just need a bleed key, a bucket to catch
the water and towel to protect carpets. Now open the bleed valves very slowly.
This will allow the water to escape and pressure to be released.